UV Air Purifier Coil Cleaner - HVAC UV Sterilizer Unit
Country of Origin︰
US $ 20 / pc
Total 49 Related Items
The EPA says indoor air quality maybe 5 times more polluted than outdoor air and even greater in high traffic areas. This unit is an ideal choice to destroy airborne virus and bacteria moving through your home or business's air conditioner system, and the destroying of spore growth (mold) growing on coils and in drain pans which greatly improves the operating efficiency of the A/C and reduces yearly operating cost.
This hospital grade UV-C (254 nm) system helps the immune compromised person and healthy person. Research studies show a 60% reduction of illness from airborne virus, bacteria, molds and neutralizes Volatile Organic Compounds (VOC's) caused by air cooling or heating systems. Ventilation systems are a superhighway for airborne pathogens to mix and contaminate the air throughout any building. Our germicidal UV system helps stop the growth of infectious airborne microbes before they cause sickness, disease and infection. Produce's no ozone.
Who can benefit from these features:
Neutropenic effects of Chemotherapy/Radiation
Some Sleeping Disorders
Doctor and Dental Office Food Manufacturing
HIV / AIDS Clinics
Meat Processing Plants Nursing Homes
Each unit is constructed for easy installation into the side of a standard air duct with minimum air velocity drop
External mounting for air handler or duct
Inspection port and safety interlock switch
BE SURE TO READ WARNINGS AND CAUTIONS BEFORE INSTALLING OR USING
YOUR UV SYSTEM
UV Light Hazard.
Harmful to bare skin and eyes.
Can cause temporary or permanent loss of vision.
Never look at bulbs while illuminated.
View illumination only through light indicator located
on lamp handle.
To prevent exposure to ultraviolet light, disconnect
power to Ultraviolet System before servicing any part
of heating and air conditioning system.
Do not mount device in location that allows ultraviolet
light to be seen after installation.
Do not attempt to bypass duct mount switch.
Do not attempt to open housing; unit is sealed to
prevent ultraviolet light exposure.
Personal Injury Hazard.
Power supply can cause electrical shock.
Disconnect power supply before cleaning or replacing
Do not open base unit or lamp handle; there are no
user-serviceable components inside.
Breakable Glass Hazard.
Can cause personal injury.
Be careful when inserting bulb(s) into lamp base.
Wear protective gloves when handling bulb(s).
UV Lamp Burn Hazard.
Harmful to bare skin.
Can cause severe burns.
Disconnect power 15 minutes before removing the
This device contains mercury in the sealed ultraviolet
bulb(s). Do not place your used bulb(s) in the trash.
Dispose of properly.
Broken Bulb Cleanup.
Do not use a household vacuum.
Sweep debris (phosphor/glass) into a plastic bag and
dispose of properly.
Contact your local waste management authority for
instructions regarding recycling and the proper
disposal of old bulb(s).
Equipment Damage Hazard.
Ultraviolet light can cause color shift or structural
degradation of plastic HVAC materials.
Select mounting location that prevents exposure to
plastic components with unknown resistance to
ultraviolet light. Three-feet minimum is recommended
between ultraviolet lamp and plastic-fabricated
devices (such as wires and non-fiberglass media
NOTE: Most drain pans and humidifiers are UV-C resistant.
Consult Honeywell’s UV exposure white paper, Form
Sharp Edges Hazard.
Can cause personal injury.
Be careful when inserting ultraviolet device into the
sheet metal cutout.
Wear protective gloves when working
When Installing this Product…
1. Read these instructions carefully. Failure to follow them
could damage the product or cause a hazardous
2. After installation is complete, check out product operation as provided in these instructions.
Selecting Mounting Location
Depending on installation location, the UV System can
operate as an Air Treatment System or as a Surface
1. The UV System can be mounted in any orientation.
2. Choose a location that is readily accessible for regular
inspection and cleaning.
3. The UV Air Treatment System requires an easily-accessible, flat mounting surface on the metal return air duct
of the HVAC system. The UV Surface Treatment System requires an easily-accessible, flat mounting surface
on the metal supply air duct of the HVAC system. The
UV Surface Treatment System must be located so the
lamp surrounds the evaporator coil and drip pan with
4. The duct mounting location must be a minimum of 8 in.
wide. See Fig. 3.
5. The depth of the duct must accommodate the full length
of the ultraviolet bulb as shown in Fig. 3.
6. The unit should be located as far away as possible from
any rubber or plastic components, such as isolators, in
If mounting options are limited, protect plastic or rubber materials listed in CAUTION with ultravioletresistant material such as aluminum foil duct tape.
7. The space adjacent to the mounting location must be
large enough to allow for ultraviolet bulb installation and
8. A 120V electrical outlet must be within range of the unit
to plug in the power cord.